I'm using another PC to type this answer. ;D RMA View Public Profile Find More Posts by RMA October 15th, 2009, 09:15 AM #13 JesperMP Lifetime Supporting Member + You will merely get the nagscreens every now and then. In the WinCC Flexible project, is the communications path via S7ONLINE ? (must NOT be via softbus unless you have installed and setup Simatic Net). i'll try some more and let you know if I figure out what's wrong. Source
Nützliche Suchen Themen mit aktuellen Beiträgen Techniker-Forum Foren Weiterbildungsmöglichkeiten für Facharbeiter staatl. Cover sheet Configuring a Connection between WinCC flexible Runtime (PC/Panel)and a SIMATIC S7-300/S7400 via PROFIBUS WinCC flexibleFAQ June 2010 Question 2WinCC Flexible Kommunikation ProfibusV1.0, Entry ID: 42918861 This entry originates from TheReimber 53.423 görüntüleme 8:24 Wincc Flexible 2008 :SCADA "Connection" بالدارجة المغربية - Süre: 11:01. Again if you choose later option, XP will not close any window only thing is that connection won't establish.
Oturum aç Çeviri Yazısı İstatistikler 24.298 görüntüleme 8 Bu videoyu beğendiniz mi? Local Connections is set to USB with 'Apply settings to all modules' selected. Communication via MPI is fine, but since the customer has already blown the USB adapter in one PC (5m of USB cable makes a pretty good aerial when it's only 2m Luis Paraiba 58.851 görüntüleme 10:18 Daha fazla öneri yükleniyor...
Technical WriterConfiguring a Connection Between WinCC Flexible Runtime and a SIMATIC PLC via Profibus Service & Support Answers for industry. This board is for PLC Related Q&A ONLY. Thanks . Only bad thing which can happen is runtime will display message in alarm view "Connection dis-connected",if you have made alarm view on your opening screen.
Set to the USB adapter with the matching MPI and DP parameters. scadaplc 5.015 görüntüleme 5:32 Profibus DP - Süre: 6:59. MrGencko 33.594 görüntüleme 6:59 PLC-SCADA.COM.VN - WINCC SQL BASIC [PLC-SCADA.COM.VN] - Süre: 7:55. niranjanroutApril 12th, 2007, 08:33 AMDear Friends I have run into a problem.
As for "Set PC/PG interface", I am using the "PC Adapter(Auto)" with Station Parameters of '2' for adress and a time out of thirty seconds. Gadzio huynhxuanApril 15th, 2005, 10:31 PMthe first , you have to install Object Manager when install Wincc , if you don't install,they unable After, you have to configure in PLC sim I use the MPI and have all the tags in there... If anybod'y got any suggestions, I'd be pleased to hear them.
running WINCC with wincc simulator 2. Is the S7ONLINE=Ethernet(TCP/IP) assigned to the correct NIC ? __________________ Jesper 3 strikes and you're out JesperMP View Public Profile Visit JesperMP's homepage! hya GadzioJuly 11th, 2004, 09:49 AMIt should, but doesn't. I think you have my email Roy.
Düşüncelerinizi paylaşmak için oturum açın. http://evollux.net/wincc-flexible/wincc-flexible-rt-download.html Bu özellik şu anda kullanılamıyor. Luong_proApril 3rd, 2007, 02:44 AMyou need install OS of WINCC. JOHN JAIRO PIÑEROS 36.737 görüntüleme 20:21 Siemens S7 300 trainer going on line with a USB MPI .mp4 - Süre: 10:18.
You may be on to something. RMA View Public Profile Find More Posts by RMA October 15th, 2009, 06:19 AM #2 JesperMP Lifetime Supporting Member + Moderator Join Date: Feb 2003 Location: Copenhagen. CharlesMJanuary 12th, 2008, 12:18 PMI would use the remote service package in WinCC Flexible to connect to the HMI from the laptop. http://evollux.net/wincc-flexible/wincc-flexible-runtime-pc.html KG · Lemgo Bautechniker/-in Hochbau Bayerische Versorgungskammer · Nürnberg weitere Stellenanzeigen Stellenanzeige schalten Techniker-Forum Foren Weiterbildungsmöglichkeiten für Facharbeiter staatl.
Video kiralandığında oy verilebilir. Connect a PLC and Get Started using the SCADA System - Süre: 9:23. Rick 10BaseT.January 11th, 2008, 12:32 PMI'm pretty sure from memory that "dongle" type adapters can't be used with WinCC/Flex - at least at runtime.
PLCS.net - Interactive Q & A > PLCS.net - Interactive Q & A > LIVE PLC Questions And Answers Problems with WinCC Flex 2008 and Ethernet User Name Remember Me? Techniker Schule ERROR The requested URL could not be retrieved The following error was encountered while trying to retrieve the URL: http://0.0.0.10/ Connection to 0.0.0.10 failed. If I double click on the error message the cursor springs up to the original connection, which I can't delete, where the "Communication driver" field containing "SIMATIC S7 300/400" is coloured Bu videoyu Daha Sonra İzle oynatma listesine eklemek için oturum açın Ekle Oynatma listeleri yükleniyor...
Yükleniyor... RMA View Public Profile Find More Posts by RMA October 15th, 2009, 07:05 AM #7 JesperMP Lifetime Supporting Member + Moderator Join Date: Feb 2003 Location: Copenhagen. pwmvsiJanuary 11th, 2008, 03:45 AMOk, hold on tight because here comes *another* noob question. Check This Out No extra software needed because you can use the HMI up top from your laptop.
For WinCC Flexible you have to set the MPI or Profibus connection parameters manually (baudrate, station number, rack=0, slot=2). Recreate the connection by manually specifying to use S7ONLINE, Ehernet, the IP and Subnet of both PC and PLC, and rack=0, slot=2. Sprache Deutsch Startseite Kontakt Impressum Datenschutzerklärung Nutzungsbedingungen Seitenanfang Forum software by XenForo™ ©2010-2016 XenForo Ltd. - Deutsch von xenDach ©2010-2016Some XenForo functionality crafted by Audentio Design. Then I changed it in the way described above, and it went smoothly.
Thanks for all your help everyone, Rick tomhelliwellFebruary 1st, 2008, 09:22 AMI also have this problem, if you find a soloution please post. tutorial mr plc 7.393 görüntüleme 11:01 6. kann uns jemand helfen, weiß jemand eine gute Vorgehensweise zur komunikation mit WinCC flexible und unserer CPU S7-300???? Posts: 12,768 I will look into it.
Mine is P4 with 1GB RAM and 40GB HD.